Main device short nameMN product or component typeVoltage release device applicationControl range compatibilityMasterpact NWMasterpact NT voltage release typeUndervoltage release [Uc] control circuit voltage48 V AC48...60 V DC Complementary threshold tripping voltage0.35...0.7 Un - during opening time0.85 Un - during closing time supply holding power4.5 VA mounting modeFixed response time40 ms Masterpact NT90 ms Masterpact NW Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
User guideSizeAdd to My Documents
No results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.