Profibus DP V1 remote master - for Premium/Quantum/M340/M580 PLC - coatedShow more characteristics >
Main range of productProfibus DP product or component typeProfibus DP V1 remote master kit compositionCD including the communication DTMCD including the Master DTM for PRM configuration inside UNITY communication gatewayEthernet Modbus TCP to Profibus DP V1 gateway product compatibilityM580 PLCPremium PLCM340 PLCQuantum PLC structure typeIndustrial bus Complementary physical interfaceRS485 method of accessMaster class 1 Profibus DPMaster class 2 Profibus DPSlave Modbus TCP mode of transmissionNRZ transmission support mediumProfibus 2 twisted shielded pairs cableModbus TCP category 5 shielded twisted pair (STP) transmission rate12 Mbit/s, 100 m bus for Profibus without repeater12 Mbit/s, 400 m bus for Profibus with 3 repeaters9.6 kbit/s, 1200 m bus for Profibus without repeater9.6 kbit/s, 4800 m bus for Profibus with 3 repeaters10...100 Mbit/s, 100 m bus for Modbus TCP without repeater number of slave126 number of inputs2 number of outputs2 communication serviceCheck slave configuration (on power up) class 1 masterManage monitoring request (Global CONTROL and Get Master Diag) class 2 masterNo master/master dialogue class 2 masterProfibus FMS message handling not supported class 1 masterProfibus FMS message handling not supported class 2 masterRead/write DP slave I/O data class 1 masterSet slave parameters (on power up) class 1 masterTransfer slave diagnostic data class 1 masterSync and freeze class 1 masterAcyclic DP V1 communication (R/W) class 1/2 master integrated connection type2 Ethernet TCP/IP - RJ45 for Modbus TCPProfibus DP - SUB-D 9 for Profibus DP V1 current consumption200 mA at 24 V DC external module formatStandard net weight0.62 kg Environment ambient air temperature for operation-25…70 °C ambient air temperature for storage-45…85 °C relative humidity10…95 % without condensation operating altitude<= 2000 m protective treatmentConformal coating Humiseal 1A33 Offer Sustainability REACh Regulation EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCatalogue Modicon M340 automation platform - English version 2014/09 (web pdf format) (Version 3.1)Modicon Quantum automation platform - English version 2015/11 (web pdf format) (Version 3.0)CertificateSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
No results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Mounting and ClearanceModule MountingAt a glance
The PRM module can be installed either:
With its support plate as a standalone module on a DIN rail, grid or panel
Without its support plate as a Premium module inside the rack
Two holes diameter 5.5 mm (7/32 in) allowing the support plate to be fixed to a panel or to an AM1-PA pre-slotted plate, with a center distance of 140 mm (5.51 in).
Tightening torque: 1 to 1.2 N-m (8.8 to 10.6 lb-in).
M4 fixing hole for securing the PRM module.
Two holes diameter 6.5 mm (0.26 in) allowing the support plate to be fixed to a panel or to an AM1-PA pre-slotted plate with a center distance of 88.9 mm (3.5 in).
Slots for positioning the pins located at the bottom and rear of the moduleMounting on a DIN rail or Plate
Installation on Drilled plate
Installation on Din rail
5.36Mounting on a Premium Rack
Mechanically, the PRM is mounted like other Premium modules. The support plate must be removed before mounting in this case.
Electrically, the PRM doesn’t use the rack connector for communication or for power supply. It must be powered by an external power supply.
To detach the module from its support plate, follow the steps below:
Unfasten the screw located in the top of the module to loosen it from itssupport.
Pivot the module forwards and disengage the pins from the holes located inthe bottom of the support.
Refer to the Premium documentation for a description of the installation on the rack.